Is standard for eye wash station?
Eyewash stations should be designed to deliver fluid to both eyes simultaneously at a volume of not less than 1.5 litres/minute (0.4 gallons/minute) for 15 minutes. The combination eye and face wash stations require 11.4 litres per minute (3.0 gallons per minute).
How much clearance is required around an eyewash station?
DO – Keep the pathway to the emergency shower and eyewash clear of obstructions. The area should be kept neat and easily accessible with at least 32 inches of clear space around a safety shower and 6 inches clearance around an eyewash.
What is required for an eyewash station?
Eyewash and Eye/Face Wash Station Requirements Plumbed station: An eye wash unit permanently connected to a continual source of potable water. Gravity-fed (self-contained) station: A stand-alone eye wash device that contains its own flushing fluid that must be refilled or replaced after use.
What are the specs for an eyewash station?
Eyewash specs Eyewash stations target just the eyes and therefore have a lower flow requirement. ANSI Z358.1 recommends a flow of 0.4 gpm also at 30 psi. The nozzles should be at least six inches from any obstruction and mounted between 33 and 45 inches above the floor.
How to use the emergency eyewash and shower station?
The following steps outline the proper use of emergency eyewash stations: Without delay, make your way to the nearest eyewash station, activate and flush eyes and/or skin for a minimum of 15 minutes. Hold eyelids open with the hands to fully irrigate the entire eye.
What is the ANSI standard for eyewash and drench shower?
Downlaod ANSI Eyewash PDF The ANSI Z358.1-2014 standard establishes a universal minimum performance and use requirements for all Eyewash and Drench Shower equipment used for the treatment of the eyes, face, and body of a person who has been exposed to hazardous materials and chemicals.
How big of a shower head do you need for eyewash?
It is recommended that the shower head be mounted between 82 and 96 inches off the floor, with the valve no higher than 69 inches. Eyewash stations target just the eyes and therefore have a lower flow requirement. ANSI Z358.1 recommends a flow of 0.4 gpm also at 30 psi.